Scholar Air Conditioners & Heat Pumps
All Scholar air conditioners and heat pumps are designed to provide quiet, efficient cooling, heating and ventilation for classrooms in a single package. The units are installed inside the classroom against an exterior wall. The vertical configuration minimizes the floor space occupied by the HVAC unit. Individual classroom units mean superior comfort and energy savings. When a central chiller/boiler system fails, an entire wing or school is affected. If a Scholar unit needs service, only one classroom is affected. When only a portion of the wing or school is being used, a large chiller/boiler system may have to operate the chiller at a reduced part load condition, the boiler for reheat and a large air handler. With Scholars, only the classroom or office being used is conditioned.
To meet fresh air requirements, a full range of ventilation options are available, including the Marvair GreenWheel® Energy Recovery Ventilator. All service and maintenance can be performed while the unit is in the classroom; moving the unit away from the wall is not required. The Scholar units can be controlled by a wall mounted thermostat or interfaced with an energy management system.
VAISA Scholar III
- IPLV: 14.0 - 14.5
- Cooling Capacities: 2 - 6 ton (24,000 BTUH - 60,000 BTUH)
Scholar III air conditioners and heat pumps (air source) are available in cooling capacities from 2 to 5 tons with a
2-stage compressor (cooling only) as standard. Electric resistance or
hot water is available as primary heat. All sizes are available for
operation on 208/230 V. 1Ø or 3Ø and 460 V. electrical supply. All
models comply with UL standard 1995, 3rd edition and listed by ETL.
VACA Scholar QV
- EER: 9.00 - 9.75
- Cooling Capacities: 2 - 5 ton (24,000 BTUH - 60,000 BTUH)
Scholar QV air conditioners and heat pumps (air source) are available as an air conditioner or heat pump with capacities of 2 to 5
tons. Electric resistance or hot water is available as primary heat on
the air conditioners and as second stage heat on the heat pump.